test code for step-voltage regulators. IEC , Insulated bushings for alternating voltages above 1 V. IEC , Tap-changers – Part 2. This part of IEC is intended to assist in the selection of tap-changers designed in accordance with IEC or IEEE Std. C for use in. Tap-changers –. Part 2: Application guide. Reference number. IEC (E). This is a free 6 page sample. Access the full version online.
|Published (Last):||6 September 2018|
|PDF File Size:||1.27 Mb|
|ePub File Size:||12.73 Mb|
|Price:||Free* [*Free Regsitration Required]|
For example, in power distribution networks, a large step-down transformer may have an off-load tap changer on the primary winding and an on load automatic tap changer on the secondary winding or windings.
If you need help with the purchase or have any queries please email enquiries standards. Tap changers exist in two primary types,  no load tap changers NLTC which must be de-energized before the turn ratio is adjusted and on load tap changers OLTC which may adjust their turn ratio during operation.
In a resistance type tap changer, the changeover must be made rapidly to avoid overheating of the diverter.
The result operates like a irc transmissionwith the tap selector switches taking the place of the gearbox and the diverter switch taking the place of the clutch. It commences operation at tap position 2, with iecc supplied directly via the right hand connection.
In other projects Wikimedia Commons. Follow these links to find other Standards similar to the one you are viewing. The disadvantage is that these tap changers are more complex and require a low voltage power supply for the thyristor circuitry.
OVE webshop – IEC
The disadvantage is that all non-conducting thyristors connected to the unselected taps still dissipate power due to their leakage currents and they have limited short circuit tolerance. Transformers with this mechanism obtain this variable turn ratio by connecting to a number of access points known as taps along either the primary or secondary winding. From Wikipedia, the free encyclopedia.
It is designed to cover every economic sector and virtually every activity of the humankind where technical standards may be used. In moving to tap 3, the following sequence occurs:.
Some arcing is unavoidable, and both the tap changer oil and the switch contacts will slowly deteriorate with use. This power consumption can add up to a few kilowatts which appears as heat and causes a reduction in overall efficiency of the transformer; however, it results in a more compact design that reduces the size and weight of the tap changer device. No load tap changers are also employed in high voltage distribution-type transformers in which the system includes a no load tap changer on the primary winding to accommodate transmission system variations within a narrow band around the nominal rating.
One possible design flag type of on load mechanical tap changer is shown to 602142 right. Amorphous metal transformer Austin transformer Autotransformer Buck—boost transformer Capacitor voltage transformer Distribution transformer Delta-wye transformer Energy efficient transformer Flyback transformer Grounding transformer Instrument transformer Current transformer Potential transformer Isolation transformer Linear variable differential transformer Pad-mounted transformer Parametric transformer Planar transformers Rotary transformer Rotary oec differential transformer Scott-T transformer Solid-state transformer Trigger transformer Variable-frequency transformer Zigzag transformer.
They are often more costly but this method is used in some modern transformers. If only one tap changer is required, manually operated tap oec are usually made on the high voltage primary or lower current winding of the transformer to minimize ifc current handling requirements of the contacts. During a tap change operation, the potential rapidly increases between the two electrodes in the bottle, and some of the energy is dissipated in an arc discharge through the bottle instead of flashing across the diverter switch contacts.
Automatic tap changers can be placed on a lower or higher voltage winding, but for high-power generation and transmission applications, automatic tap changers are often placed on the higher voltage lower current transformer winding for 6021-2 access and to minimize the current load during operation. Agbioeletric Balun Buchholz relay Bushing Center tap Circle diagram Condition monitoring of transformers Copper loss Dissolved gas analysis Electrical insulation paper Growler High-leg delta Induction regulator Leakage inductance Magnet wire Metadyne Open-circuit test Polarity Polychlorinated biphenyl Quadrature booster Resolver Resonant inductive coupling Severity factor Short-circuit test Stacking factor Synchro Tap changer Toroidal inductors and transformers Transformer oil Transformer oil testing Transformer utilization factor Vector group.
Ief prevent contamination of the tank oil and facilitate maintenance operations, the diverter switch usually operates in a separate compartment from the main transformer tank, and often the tap selector switches will be located in the compartment as well. This prevents arcing ic the main contacts and can ice to a longer service life between maintenance activities.
September Learn how and 6024-2 to remove this template message. In a typical diverter switch, powerful springs are tensioned by a low power motor motor drive unit, MDUand then rapidly released to effect the tap changing operation. Solid state tap changers are typically employed only oec smaller power transformers.
The low voltage tap may be requested to change positions multiple times each day, without interrupting the power delivery, to follow loading conditions on the low-voltage secondary winding network.
International Classification for Standards ICS is an international classification system for technical standards. The high voltage tap is set to match long term system profile on the high voltage network typically supply voltage averages and is rarely changed.
In such systems, the tap 602142 will often be set just once, at the time of installation, although it may be changed later to accommodate a long-term change in the system voltage profile.
Articles lacking in-text citations from September 6214-2 articles lacking in-text citations Commons category link is on Wikidata. We recommend that you check the website of the publishers of the international document before making a purchase.
IEC 60214-2 Ed. 1.0 en(2004)
A reactance type tap changer uses a dedicated preventive autotransformer winding to function as the diverter impedance, and a reactance type tap changer is usually designed to sustain off-tap loading indefinitely. On load tap changers may be generally classified as either mechanical, electronically assisted, or fully electronic.
Assists in the selection of tap-changers designed in accordance with IEC for use in conjunction with the tapped windings of transformers or reactors. This article includes a list of referencesbut its sources remain unclear because it has insufficient inline citations.
Application guide This document has been re-assessed by the committee, and judged to still be up to date. This technique overcomes the problems with open or short circuit taps.
Diverter resistor A is short-circuited; diverter B is unused. It is important to us that you purchase the right document. Safety of power transformers, power supply units and similar – Particular requirements – Particular requirements for isolating transformers and power supply 60214- incorporating isolating transformers You may be interested in this related standard Safety of transformers, reactors, power supply units and similar products for supply voltages up to 1 V — Part 2.
A mechanical tap changer physically makes the new 60214- before releasing the old using multiple tap selector switches but avoids creating high circulating currents by using a diverter switch to temporarily place a large diverter impedance in series with the short-circuited turns. Thyristor-assisted tap changers use thyristors to take the on load current while the main contacts change over from one tap to the next. This is a relatively recent development which uses thyristors idc to switch the ieec winding taps and to pass the load current in the steady state.
Retrieved from ” https: Covers both on-load tap-changers and off-circuit tap-changers. Tap changers typically use numerous tap selector switches which may not be switched under load, broken into even and odd banks, and switch between the banks with a heavy-duty diverter switch which can switch between them under load. Reactance-type tap changers, when operating in oil, must allow for the additional inductive transients generated by the autotransformer and commonly include a vacuum bottle contact in parallel with the diverter switch.